References in periodicals archive ?
For the power segment, the combined energy sales of SCPC and SLPGC increased 11 percent to 638 gigawatt-hours (gwh).
Meanwhile, SLPGC 2 blamed 'primary air fan, high stator winding temperature and primary air fan B high motor bearing vibration' as the cause of the outage.
(There has been a simultaneous breakdown of the Sual power plant, Calaca power plant, the Pagbilao power plant and even the Malaya thermal power since 2012, but there were also new ones breaking down like the SCPC, SLPGC at SLTEC.)
The power plants that suffered operational malfunctions had been gridlocked with technical problems ranging from boiler tube leak for SLTEC; vibration in primary air fan for SLPGC; and boiler slagging for Pagbilao-3, according to the DOE.
The other plants serving the Luzon grid but have de-rated capacity are Calaca coal-plant 2 at 200 MW (from 300 MW) and SLPGC 2 at 100 MW (from 150 MW).
Unit 2 of SLPGC was also shut down for preventive maintenance work.
The derated plants are Calaca 2 at 200 MW from its declared 300 MW capacity, and SLPGC 2 at 100 MW from 150 MW.
Southwest Luzon Power Generation Corp.'s (SLPGC) gross generation dropped 19 percent year on year to 1,368 GWH from 1,687 GWH.
(SLPGC) contributed P5.9 billion, P4.5 billion and P1.6 billion, respectively.
Acronyms browser ?
Full browser ?
- SLP-76 tyrosine phosphoprotein